Heat Shrinkable Cable Termination
Standard; IEC60442: 1997
Main material: Polyolefin
*Indoor, outdoor, straight joint
1. Flame-retardant, rapid shrinking, non-cracking, and simple installation.
2. Highly resistance to extreme temperature, atmospheric pollution and weather conditions.
3. Insulation components are resistant to fungus, copper corrosion, water and ultra-violet rays.
4. Hot melting adhesed lining in insulation components provides excellent waterproofing property.
2 Heat Shrinkable Sleeves
3 Rain Sheds
4 Earthing Wire
5 Silicone Grease
6 Stress Relieving Mastic
7 Filling Mastic Strip/Sealing Mastic Strip
8 Triangle Cone-cushion
9 Sealing Tubing
10 Anti-tracking Tubing
11 3-hole Rain Shed
12 Stress Control tubing
13 Phase Marking Sleeves
14 Assistant Material
Items Standard Requirements Test Result Remarks AC withstand 45kV, 1min no flashover no breakdown 45kV, 1min, no breakdown and flashover occurred OK Partial discharge test 13kV, ≤10pC Phase yellow Green Red pC ≤3pC ≤3pC ≤3pC OK Impulse voltage withstand 105kV, at 10 positive and 10 negative impulses, no flashover no breakdown 105kV, no flashover and breakdown occurred OK DC withstand 52kV, 15min no flashover no breakdown 52kV, 15min no flashover no breakdown occurred OK Thermal short- circuit (conductor) 20kA, 2s, no transfigure and welding on all parts 20kA, 2s, no transfigure and welding occurred on all parts OK Dynamic short- circuit 50kA, 0. 3s, no transfigure and welding on all parts 50kA, 0. 3s, no transfigure and welding on all parts OK